Comparison between a STATCOM and SVC
- The SVC results in the following benefits:
- voltage support,
- transient stability improvement, and
- power system oscillation damping
- The STATCOM generates a three-phase voltage source with controllable amplitude and phase angle behind a reactance. When the AC output voltage from the inverter is higher (lower) than the bus voltage, the current flow is caused to lead (lag), and the difference in the voltage amplitudes determines how much current flows. This allows the control of reactive power.
Comparison Between Statcom And Svc
The main difference between a STATCOM and an SVC is the way they operate: a STATCOM works as a controllable voltage source while an SVC works as a dynamically controllable reactance connected in parallel.
Compared with an SVC, a STATCOM offers the possibility of feeding the grid with the maximum available reactive current even at low voltage levels, this is possible because in every equilibrium condition, the injected reactive power varies linearly with the voltage at the Point of Common Coupling (PCC). In contrast, for an SVC there is a quadratic dependence of the reactive power on the voltage at the PCC which means that to inject the same reactive power it is necessary to install an SVC with a nominal capacity higher than that of a STATCOM.
With regard to the maximum transient capacitive current, it is observed that in an SVC the capacitive current is limited by the size of the capacitor and by the magnitude of the AC voltage. In the case of a STATCOM, the maximum capacitive current that can be injected is limited by the maximum current capacity of the semiconductors used and is independent of the voltage level at the PCC.
Another feature of a STATCOM is that the DC-link capacitor serves as storage for active power. Therefore in certain situations, depending on the capacitor size, it is possible to regulate the interchange of active power with the grid also.
STATCOM devices are capable of much faster dynamic reaction (1/4-1 cycle) than an SVC. In a STATCOM the speed of response is limited by the commutation frequency of the IGBTs (normally 1 kHz).
Related Topic – click here
- What Is A Diode? Working Principle & Types | Different Types Of Resistors
- What Is Synchronous Speed? | Types & Advantages Of DC Motors
- Working Principle Of Linear Variable Differential Transformer | Construction & Piezoelectric Transducers
- Three-Phase Induction Motor | 3-Phase Induction Motor Principle
- Introduction To Electrical Transformer | Definition, Construction & Parts Of A Transformer | Types Of Transformers
- DC Generator | Principle Of Operation, Construction, Types Of Generators & Application
- What Is DC Motor? | Principle Of DC Motor & Types Of DC Motors
- Diode-Circuits |Diode Convention, Transformer Rectifier & Objective Questions With Answer